Kwikon® electrical fittings | slab boxes | accessories
Noncorroding and nonconducting, Kwikon Fittings are engineered for the toughest challenges of the construction industry. Kwikon fittings can be encased in concrete, concealed in walls or ceilings, or in direct burial applications. Both Kwikon couplings and connectors, with their unique 360º locking tabs, provide for snap-on, lock-in installation that exceeds CSA and UL requirements for conduit pullout. Add our innovative form stubbys and Kwikon concrete-tight slab boxes, (available with or without integral 1⁄2″, 3⁄4″ or 1″ molded hub connectors) and you’ve got a total integrated system that saves you time and money on the job.
Featured Case Study
The Revitalization of Bronte village proudly supported by IPEX Electrical. In the spring of 2019, construction began on two new towers at Bronte Village in Oakville, Ontario. The 10- and 14-storey towers include 487 housing units, five retail spaces, and two guest suites
Discover more about IPEX
Our resources section covers everything you need to know: Take a look at our most popular resources below
A. Standards referred to in this section are:
CSA Standards C22.2, No. 227.1 and C22.2 No. 85.
NEMA TC-13 Electrical Nonmetallic Tubing.
A. Acceptable manufacturers are listed below
1. Electrical Nonmetallic Tubing:
a. Cor-Line by IPEX
2. Electrical Nonmetallic Tubing Fittings:
b. Kwikon by IPEX
3. Electrical Nonmetallic Tubing Boxes:
c. Kwikon by IPEX
B. All ENT tubing, ENT fittings, ENT boxes and accessories shall be manufactured by the same company so as to form a complete ENT system.
C. ENT systems shall be approved for use in fire resistance rated concrete floor-ceiling assemblies with fire resistance ratings up to 4 hours.
A. ENT raceway shall be listed to CSA C22.2 No. 227.1 and manufactured in accordance with NEMA TC-13.
A. ENT Fittings shall be manufactured of high-impact PVC.
B. ENT Fittings shall meet the following requirements:
Six locking tabs located every 60º providing 360º contact.
Locking tabs shall provide a conduit pullout of a minimum 175 ft-lb force.
Concrete tight without the need for taping.
When transitioning to EMT conduit, the transition fitting shall have six locking tabs for ENT connection and set-screw connection for EMT.
A. ENT boxes shall be manufactured of high-impact PVC.
B. ENT Slab Box and Wall Box requirements:
Slab Boxes shall be approved for the purpose and concrete-tight.
Slab Boxes shall have eight (8) integrally molded ENT hub connectors with six locking tabs for ENT raceway connection.
ENT raceways, fittings, boxes and accessories shall be installed in accordance with the 2009 Canadian Electrical Code, Part 1 – C22.1-02 (CEC) and the 1995 National Building Code of Canada (NBC).
Where ENT penetrates a fire-rated wall, floor or ceiling assembly, an approved firestop system is CSA certified to CSA Standards C22.2, No. 211.0. See Codes & Standards for additional installation information.
1⁄2″ – 2-1⁄2″
CSA C22.2 No.18
CSA C22.2 No.85
CSA C22.2 No.227.1
CSA C22.2 No.227.2
UL 514C, 1653
FT-4 rated for use in non-combustible construction
Residential (Low or High Rise)
Commercial (Low or High Rise)
Institutional (Prisons, Schools, Universities)
Hospitals and Nursing Homes
Stadiums and Arenas